Sundance Chelsee Won't Start
Posted 23 October 2010 - 10:37 AM
Posted 23 October 2010 - 01:20 PM
Error codes by manufacturer;
"Men nearly always believe what they wish to be true"
"Having the best price, the best service, and the best quality all at once is impossible"
Posted 23 October 2010 - 03:20 PM
Posted 24 October 2010 - 03:27 PM
The GFI breaker keeps tripping and no power at spa. We disconnected power at spa control box and GFI breaker stays on, but if we hook power back up to spa breaker trips. spa worked great last weekend, we use it weekly.
You have a ground fault somewhere in the tub. Usually, it is a heater or ozonator (if equipped). Do not keep putting power to this particular board or you will damage it and dramatically escalate your repair costs. The proper method of ground fault testing is to isolate each load and ground fault test with a megohmmeter. The 356 is NOT an error code.
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users